for Malakoff, TX
Our Reviews by City
Air conditioning installation, maintenance and service. No cool, found unit low on refrigerant. Performed leak search, repaired leak and filled with refrigerant. Installed new wifi thermostat
Ac service call, checked freon levels, coil integrity, and all electrical parts of the system
Heating maintenance call on 4&2-ton Carrier Heatpump system.Inspected evaporator coils,blower motor&wheels,electrical wiring,duct systems,thermostats,line set,drain pain,cleared drain lines,clean condensor units and refrigerant charge on systems.Start up and check operation of systems.
Changing out electric heater and straight AC. Both of the originals were 20 yrs old.